This product has good explosion-proof function, suitable for IIA, IIB, IIC explosive gas environment and various inflammable and explosive places, mainly used in railway, electric power, metallurgy, petroleum, petrochemical, chemical, steel, aviation, ship and each Efficient lighting in factories, stations, large facilities, venues and other places.
(1) Configuration: It adopts imported LED light source, with an average service life of up to 100,000 hours. The power supply adopts wide voltage processing, which can realize constant current output, and has short-circuit and over-voltage protection functions, which greatly prolongs the service life of the lamps.
(2) Heat dissipation: The heat sink adopts an integrated streamline structure to better increase heat conduction. The heat sink is arranged in an array of inner and outer circumferences to improve heat dissipation performance.
(3) Anti-glare: tempered glass cover (transparent and matte two optional methods) adopts honeycomb-shaped crystallization point anti-glare design, which makes the light even and soft without shadow, and the light transmittance is as high as 95%-98%, suitable for various low Top, platform, high ceiling, high shed and other places are used as solid lighting.
(4) Protection: The protection level of the lamp body is IP66, and the anti-corrosion level can reach WF2. The surface of the lamp body will never corrode and never rust.
(5) Installation method: Various installation methods such as ceiling, ceiling, curved rod and pole can be used as needed.
(6) Inlet: The double inlet port design can realize the series connection and installation of the lamps.
|Explosion proof grade||ExdIICT6|
Picture of real products
1.Before installation, it is necessary to check whether the actual operating conditions are in conformity with the parameters listed on the lamp nameplate.
2.Before installation, please test the lighting according to the parameters of the lamp nameplate to ensure that there is no quality problem before installation.
3.Before installation, it is necessary to determine the installation location and mode of the lamps according to the installation mode provided by the product, in combination with the on-site use environment and lighting requirements, so as to ensure that the installation is firm and reliable.
4.Connect the prepared cables with the input cables of lamps and lanterns according to the corresponding fire (brown), zero (blue) and ground (yellow-green) wires, so as to ensure that the connection is firm, and make good insulation and waterproof measures at the connection.
5.The input end of the cable can be connected to the power supply of the corresponding voltage to illuminate.
Using the matters needing attention
1. This product is an explosion-proof product and can be used in explosion-proof places.
2. When transporting, the lamp should be installed in the carton equipped with foam shock absorption.
3. When using, the surface of the lamp has a certain temperature rise, which is a normal phenomenon.
4. The power supply voltage can work normally in the rated voltage. If the power supply voltage is too high, the lamp will be damaged; if the voltage is too low, the lamp will not start normally.
5. The luminaire must be reliably grounded.